The customer called our Pump Repair number and said their pump...Read More
Upper Kedron - House Pump Cycling
The customer called our Pump Repair number and said their pump had been turning on and off quite frequently over the past week. After investigating further about the pumps installation date and position, I had a good idea what the problem was and how to fix it. Due to the style and age of the pump, I could tell the Air Tank was faulty and would either need replacing or adjusting the air pressure.
I arrived at the house, tested the air tank and found it was faulty beyond repair and needed replacing. I replaced the Air Tank, adjusted the air pressure to suit the pumps requirements and tested the pump to ensure it was operating correctly.
n.b. Not all situations will be solved through the same solution, even if you are experiencing similar problems it may need a completely different solution. It is recommended you contact a Pump Technician to assist you.